You get all the advantages of perfect quality water with Ecosoft MO12000 Econnect commercial reverse osmosis system. It is the most advanced and effective way to remove up to 99.8% of impurities, including bacteria and viruses. Reverse osmosis is an eco-friendly and economic way to get safe drinking water.
The system is a compact and entirely functionally complete module.
New unique ECONNECT function turns commercial reverse osmosis system for water purification into modern smart device.
Each user has personal online directory with full information about system:
─ effectiveness statistics and analysis of operation
─ real-time system status
─ possibility of adjusting settings remotely
Apart from the main information about feed water quality and the amount of purified water, the personal online directory holds available data about membrane element effectiveness and status
A new OC6000 multifunctional controller is installed in each Ecosoft MO 12000 Econnect commercial reverse osmosis system. It sends all data available in the personal online directory.
Up to 12000 liters of purified water per day
Continuous monitoring of purified water quality
Compact and fully automated
High-quality components from leading manufacturers
Low noise and vibration high pressure pump
Improved ОС6000 controller for constant independent operation of the system
Controller ОС 6000 — best possibilities for professional maintenance:
— measures the flow rate and volume of purified water;
— quality of feed water and treated water;
— purified water discharge mode;
— remote update of firmware.
With ECONNECT functionality, system maintenance becomes easier and more effective!
A history of system maintenance and operation in the personal online directory will allow the most efficient and timely replacement of filters, chemical washing of membranes and other system maintenance activities.
● Replace the sediment filters — at least once every 3 months.
The sediment filter protects the RO membrane from large impurities such as sand, clay particles, etc. With the ECONNECT function you will always know when to replace them. Now your membrane element and system will last much longer.
● Carry out chemical cleaning of the RO membrane — at least twice a year.
CIP should be carried out in case of deteriorating purified water quality or capacity reduction, which you can observe in the personal online directory. CIP is carried out by using a chemical cleaning unit and cleaning chemicals.
You don’t need to keep a system maintenance log any more!
Timely maintenance expands the lifetime of the equipment, but also provides pure and safe water of the highest quality.
Who is the product for?
Ecosoft MO 12000 Econnect RO system is designed for water purification in:
— hotels, cafes, and restaurants;
— brewery and bakery;
— laboratories and workshops;
— car wash;
— small scale industrial processes;
— steam boilers, heating and cooling systems.
Inside the membrane module of the installation, water is divided into two streams:
— demineralized water — permeate
— high salt water — concentrate
Part of the concentrate during operation of the module is discharged into the sewer system, and the rest is sent to the inlet of the high pressure pump, providing the so-called recycling of the concentrate.
An antiscalant can be dosed into the feed water stream, which prevents the formation of deposits inside the membrane elements.
Before reverse osmosis, the water undergoes preliminary cleaning on a fine filter cartridge, preventing ingress of impurities larger than 5 microns on the membrane.
The system is operated by the controller and provides:
— automatic switching on and off of the equipment upon signal from the level sensor in the permeate collector or pressure in the permeate line with preliminary hydraulic flushing;
— emergency shutdown of the equipment by signals from dry-running sensors, overpressure in the module;
— shutdown of equipment on the external STOP signal;
— hydraulic flushing of membranes;
— permanent quality control (electrical conductivity and temperature) of permeate.
Sediment filters protect the membrane from large impurities such as sand, clay particles, etc. Failure to replace the filters in due time can damage or destroy the membrane. In order to avoid such critical situations, we recommend changing the filter at least once every 3 months..
In case of worsening quality of the treated water or a decrease in productivity, it is necessary to conduct chemical cleaning of the RO membrane with a CIP-station and special reagents. To obtain purified water of high quality, we recommend chemical cleaning at least twice a year.
If you do not plan to use the system for a long time, it is necessary to shut off the water supply to the system, and soak the membrane elements in a special preservative solution – this will keep the membranes working when the equipment is not in use.
Operational characteristics and technical data
|Flow capacity at 15°С1
|230 V, 50 Hz
|Operation pressure in the RO membrane
|Water consumption in operating mode
|Water consumption in flush mode
|Connection port sizes:
- feed water
|System dimensions (H x W x D), mm
|540 х 405 х 1450
1 capacity of the RO system depends on feed water composition and its temperature
2 for stable operation requires a constant pressure (+/- 0.5 bar) in the specified range
Feed water requirements
|Temperature of feed water
|Residual chlorine, max
|Chemical oxygen demand
|mg O2/L (ppm O2)
1 when using antiscalant, hardness and silica have higher limits
2 for reliable operation stable pressere needed (+/- 0.5 bar)
Components of the system
- Dow Filmtec™ XLE-4040 membrane
- Grundfos high-pressure pump
- European solenoid valves
- Multifunctional controller
- Conductivity sensor
- Sediment filter
- High and low-pressure switches
- Float switch
- Regulated discharge and recycle flow meter
- Vibration resistant pressure gauges
- Frame with unique design
- Dow Filmtec™ LC LE-4040 membranes
- Membrane rinse with permeate
- Raw water blending